generic_thermostat climate platform is a thermostat implemented in Home Assistant. It uses a sensor and a switch connected to a heater or air conditioning under the hood. When in heater mode, if the measured temperature is cooler than the target temperature, the heater will be turned on and turned off when the required temperature is reached. When in air conditioning mode, if the measured temperature is hotter than the target temperature, the air conditioning will be turned on and turned off when required temperature is reached. One Generic Thermostat entity can only control one switch. If you need to activate two switches, one for a heater and one for an air conditioner, you will need two Generic Thermostat entities.
# Example configuration.yaml entry climate: - platform: generic_thermostat name: Study heater: switch.study_heater target_sensor: sensor.study_temperature
entity_id for heater switch, must be a toggle device. Becomes air conditioning switch when
ac_mode is set to
entity_id for a temperature sensor, target_sensor.state must be temperature.
Set initial target temperature. Failure to set this variable will result in target temperature being set to null on startup. As of version 0.59, it will retain the target temperature set before restart if available.
Set the switch specified in the heater option to be treated as a cooling device instead of a heating device.
Set a minimum amount of time that the switch specified in the heater option must be in its current state prior to being switched either off or on.
Set a minimum amount of difference between the temperature read by the sensor specified in the target_sensor option and the target temperature that must change prior to being switched on. For example, if the target temperature is 25 and the tolerance is 0.5 the heater will start when the sensor equals or goes below 24.5.
Set a minimum amount of difference between the temperature read by the sensor specified in the target_sensor option and the target temperature that must change prior to being switched off. For example, if the target temperature is 25 and the tolerance is 0.5 the heater will stop when the sensor equals or goes above 25.5.
Set a keep-alive interval. If set, the switch specified in the heater option will be triggered every time the interval elapses. Use with heaters and A/C units that shut off if they don’t receive a signal from their remote for a while. Use also with switches that might lose state. The keep-alive call is done with the current valid climate integration state (either on or off).
Set the initial HVAC mode. Valid values are
cool. Value has to be double quoted. If this parameter is not set, it is preferable to set a keep_alive value. This is helpful to align any discrepancies between generic_thermostat and heater state.
Set the temperature used by
preset_mode: away. If this is not specified, the preset mode feature will not be available.
keep_alive must be set as “hh:mm:ss” or it must contain at least one of the following entries:
milliseconds:. Alternatively, it can be an integer that represents time in seconds.
generic_thermostat climate platform supports ‘heat’, ‘cool’ and ‘off’ HVAC modes. You can force your
generic_thermostat to avoid starting by setting HVAC mode to ‘off’.
Please note that when changing the preset mode to away, you will force a target temperature change as well that will get restored once the preset mode is set to none again.
climate: - platform: generic_thermostat name: Study heater: switch.study_heater target_sensor: sensor.study_temperature min_temp: 15 max_temp: 21 ac_mode: false target_temp: 17 cold_tolerance: 0.3 hot_tolerance: 0 min_cycle_duration: seconds: 5 keep_alive: minutes: 3 initial_hvac_mode: "off" away_temp: 16 precision: 0.1